Main range of productAdvantys Telefast ABE7 product or component typeSolid state input relay sub-base [Us] rated supply voltage24 V DC (PLC end)24 V DC (sensor end) number of channels16 number of terminal per channel2 connections - terminalsScrew type terminals, clamping capacity: 1 x 0.09...1 x 1.5 mm², cable cross section: 0.09...1.5 mm² AWG 28...AWG 16 flexible with cable endScrew type terminals, clamping capacity: 1 x 0.14...1 x 2.5 mm², cable cross section: 0.14...2.5 mm² AWG 26...AWG 12 solidScrew type terminals, clamping capacity: 1 x 0.14...1 x 2.5 mm², cable cross section: 0.14...2.5 mm² AWG 26...AWG 14 flexible without cable endScrew type terminals, clamping capacity: 2 x 0.09...2 x 0.75 mm², cable cross section: 0.09...0.75 mm² AWG 28...AWG 20 flexible with cable endScrew type terminals, clamping capacity: 2 x 0.2...2 x 2.5 mm², cable cross section: 0.2...2.5 mm² AWG 24...AWG 14 solid Complementary terminal block typeRemovable supply voltage limits19...30 V DC (PLC end) conforming to IEC 61131-2 isolation PLC/operative partYes protection typeInternal fuse of 1 A (5 x 20 mm), fast blow type at PLC endAdjustable by external fuse, fast blow type at sensor end fixing modeBy clips on 35 mm symmetrical DIN railBy screws on solid plate with fixing kit current per channel0.012 A current state 1 guaranteed>= 2 mA (sensor end) voltage state 1 guaranteed>= 15 V (sensor end) maximum switching current15 mA (PLC end) minimum switching current1 mA (PLC end) response time<= 0.05 ms from state 0 to 1<= 0.4 ms from state 1 to 0 switching frequency<= 1000 Hz duty cycle: 50 % [Uimp] rated impulse withstand voltage2.5 kV conforming to IEC 60947-1 [Ui] rated insulation voltage2000 V installation categoryII conforming to IEC 60664-1 tightening torque0.6 N.m (with flat Ø 3.5 mm) product weight0.37 kg Environment dielectric strength2000 V 50/60 Hz conforming to IEC 60947-1 product certificationsBVCSADNVGLLROS (Lloyds register of shipping)UL standardsIEC 61131-2 Type 1 IP degree of protectionIP2x conforming to IEC 60529 resistance to incandescent wire750 °C conforming to IEC 60695-2-11 shock resistance15 gn for 11 ms conforming to IEC 60068-2-27 vibration resistance2 gn (f = 10...150 Hz) conforming to IEC 60068-2-6 resistance to electrostatic discharge4 kV (contact) conforming to IEC 61000-4-2 level 38 kV (air) conforming to IEC 61000-4-2 level 3 resistance to radiated fields10 V/m (26000000...1000000000 Hz) conforming to IEC 61000-4-3 level 3 resistance to fast transients2 kV conforming to IEC 61000-4-4 level 3 ambient air temperature for operation-5...60 °C conforming to IEC 61131-2 ambient air temperature for storage-40...80 °C conforming to IEC 61131-2 pollution degree2 conforming to IEC 60664-1 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsPremium automation platform - Telefast 2 - Sub-bases (Version 1.0)BrochureSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsMarine certificateSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsDimensions(1)ABE7BV20 / ABE7BV20E
Mounting and ClearanceMounting
Connections and SchemaHE10 16 ChannelsWiring Diagram
S16E2B1 / E2B1E
S16E2E1 / E2E1E
S16E2E0 / E2E0E
S16E2F0 / E2F0E
S16E2M0 / E2M0E
Performance CurvesCurves for Determining Cable Type and Length According to the Current16-channel Sub-baseLCable lengthITTotal current per sub base (A)IAAverage current per channel (mA)(1)TSXCDP••2 and ABFH20H••0 cables with c.s.a. 0.08 mm2 (AWG 28).(2)TSXCDP••3 cables with c.s.a. 0.34 mm2 (AWG 22).(3)Cables with c.s.a. 0.13 mm2 (AWG 26).
The curves are given for a voltage drop of 1 V in the cable. For n volts tolerance, multiply the length determined from the graph by n.